About the Department
Department Organizational Chart
Police Leadership History
Rave Guardian Safety App
Personal Safety Tips
Residential Safety Program
Sexual Assault Education
Campus Facilities Access
Substance Abuse Education
Integrated Emergency Planning
Campus Crime Information
Campus Crime Report
Campus Security Authority
Daily Incident/Fire Log
Clery Timely Warnings
Emergency Notification System
Citizen Compliment & Complaint
Making a Complaint
Statistical Summary of Complaints
Forms and Policy
Substance Abuse Policy
Sexual Assault/Sexual Harassment Policy
Presentation Request Form
Campus Free Speech Guidelines
U.S. Department of Labor
Program Highlight - Fact Sheet No. OSHA 91-41
Fire safety is important business. National Fire Prevention Week is intended to focus on the importance of fire safety in the home, in schools and at work. But workplace fire safety is the Occupational Safety and Health Administration's (OSHA) principal focus and saving lives and preventing injuries due to fire is a key concern.
According to National Safety Council figures, losses due to workplace fires in 1988 totaled $3.1 billion. Of the more than 5,000 persons who lost their lives due to fires in 1988, the National Safety Council estimates 360 were workplace deaths.
There is a long and tragic history of workplace fires in this country. One of the most notable was the fire at the Triangle Shirtwaist Factory in New York City in 1911 in which nearly 150 women and young girls died because of locked fire exits and inadequate fire extinguishing systems.
History has repeated itself recently in the fire in Hamlet, North Carolina, where 25 workers died in a fire in a poultry processing plant. It appears that here, too, there were problems with fire exits and extinguishing systems.
When OSHA conducts workplace inspections, it checks to see whether employers are complying with OSHA standards for fire safety.
OSHA standards require employers to provide proper exits, fire fighting equipment, emergency plans, and employee training to prevent fire deaths and injuries in the workplace.
Building Fire Exits
- Each workplace building must have a full complement of the proper type of fire extinguisher for the fire hazards present.
- Employees expected or anticipated to use fire extinguishers must be instructed on the hazards of fighting fire, how to properly operate the fire extinguishers available, and what procedures to follow in alerting others to the fire emergency.
- Only approved fire extinguishers are permitted to be used in workplaces, and they must be kept in good operating condition. Proper maintenance and inspection of this equipment is required of each employer.
- Where the employer wishes to evacuate employees instead of having them fight small fires there must be written emergency plans and employee training for proper evacuation.
Emergency Evacuation Planning
- Each employer needs to have a written emergency action plan for evacuation of employees which describes the routes to use and procedures to be followed by employees. Also procedures for accounting for all evacuated employees must be part of the plan. The written plan must be available for employee review.
- Where needed, special procedures for helping physically impaired employees must be addressed in the plan; also, the plan must include procedures for those employees who must remain behind temporarily to shut down critical plant equipment before they evacuate.
- The preferred means of alerting employees to a fire emergency must be part of the plan and an employee alarm system must be available throughout the workplace complex and must be used for emergency alerting for evacuation. The alarm system may be voice communication or sound signals such as bells, whistles or horns. Employees must know the evacuation signal.
- Training of all employees in what is to be done in an emergency is required. Employers must review the plan with newly assigned employees so they know correct actions in an emergency and with all employees when the plan is changed.
Fire Prevention Plan
- Employers need to implement a written fire prevention plan to complement the fire evacuation plan to minimize the frequency of evacuation. Stopping unwanted fires from occurring is the most efficient way to handle them. The written plan shall be available for employee review.
- Housekeeping procedures for storage and cleanup of flammable materials and flammable waste must be included in the plan. Recycling of flammable waste such as paper is encouraged; however, handling and packaging procedures must be included in the plan.
- Procedures for controlling workplace ignition sources such as smoking, welding and burning must be addressed in the plan. Heat producing equipment such as burners, heat exchangers, boilers, ovens, stoves, fryers, etc., must be properly maintained and kept clean of accumulations of flammable residues; flammables are not to be stored close to these pieces of equipment.
- All employees are to be apprised of the potential fire hazards of their job and the procedures called for in the employer's fire prevention plan. The plan shall be reviewed with all new employees when they begin their job and with all employees when the plan is changed.
Fire Suppression System
- Properly designed and installed fixed fire suppression systems enhance fire safety in the workplace. Automatic sprinkler systems throughout the workplace are among the most reliable fire fighting means. The fire sprinkler system detects the fire, sounds an alarm and puts the water where the fire and heat are located.
- Automatic fire suppression systems require proper maintenance to keep them in serviceable condition. When it is necessary to take a fire suppression system out of service while business continues, the employer must temporarily substitute a fire watch of trained employees standing by to respond quickly to any fire emergency in the normally protected area. The fire watch must interface with the employers' fire prevention plan and emergency action plan.
- Signs must be posted about areas protected by total flooding fire suppression systems which use agents that are a serious health hazard such as carbon dioxide, Halon 1211, etc. Such automatic systems must be equipped with area pre-discharge alarm systems to warn employees of the impending discharge of the system and allow time to evacuate the area. There must be an emergency action plan to provide for the safe evacuation of employees from within the protected area. Such plans are to be part of the overall evacuation plan for the workplace facility.
This is one of a series of fact sheets highlighting U.S. Department of Labor programs. It is intended as a general description only and does not carry the force of legal opinion.